Application and Dosage
The recommended ‘in use’ concentration of the product is 0.5%. One 500ml bottle will treat an average 130-litre system (up to 16 single radiators). The product can be dosed into the system via the Fernox TF1 filling point, the system filling loop or the radiator using a Fernox Injector and circulate. Fernox Filter Fluid+ Protector liberates system contaminants and delivers them to an in-line filter for removal. Once all the work is complete on the heating system, the final action that we recommend is carried out, is to isolate the filter & empty collected contaminants. Fernox Filter Fluid+ Protector should remain in the system. It is not for use in microbore systems. For heavily sludged systems or new installations, Fernox recommends cleaning and flushing using Fernox Cleaner F3/F5 before treating with Filter Fluid+ Protector/ Protector F1 and installing a filter. The installation of a system or new boiler should comply with all local legislation such as Part L of the Building Regulations For continued protection, it is recommended Fernox Protector levels are checked annually as part of any filter maintenance programme. Filter Fluid+ Protector should only be used when a system filter has been installed.
Fernox Filter Fluid+ Protector is a blend of corrosion and scale inhibitors and dispersants
pH (conc): 8.0
pH (in use): 7.0-8.0
Packaging, Handling and Storage
Fernox Filter Fluid+ Protector is supplied in 500ml containers or 400ml aerosol cannister. Fernox Filter Fluid+ Protector is classified as non-hazardous, but as with all chemicals: Keep out of reach of children. Do not mix with other chemicals. Contains 1,2-benzisothiazol-3(2H)-one. May produce an allergic reaction.